We get asked all the time, "why is the voltage of the one line so much higher than the other two?" All traditional phase converters are high leg delta. This means that when using your meter you will measure 120 volts to ground on two of the three lines, but around 240 volts to ground on the third. This is perfectly normal and will work just fine for most motor loads.
Here are some pictures of what you might be seeing.
Traditional phase converters create only the 3rd line. The other two lines are left untouched.
In a phase converter, the two single-phase lines from the utility pass through untouched. After going through the converter, they will remain at the same voltage and will still be 180 degrees out of phase from each other.
The phase converter will add line 3. This is called the "manufactured leg". If you measure this 3rd line to the ground then it will be much higher than the other two lines. This is totally normal.
The phase converter doesn't create a new "reference" to ground. The only thing the converter does is create line 3 a.k.a. the "manufactured leg".
In your single phase electrical panel, line 1 and 2 have a neutral which is bonded to ground ( usually the water or gas line) and in turn gives you your reference to ground.
When you measure to ground from either of these two lines you will see 120 volts. However, when you measure line 3 to ground, then you are actually referencing the ground that is between line 1 and 2 so it makes sense that you would get a different reading.
This type of electrical configurations is often referred to as High Leg Delta. High leg delta electrical services can still be found in older industrial and rural locations.
This 3 phase utility configuration is called "high leg delta" because the triangle looks like a delta Δ and line 3 (a.k.a. leg 3) is at higher voltage potential to ground than the other two lines.
If you were to measure line-to-line, then you will see that they are all the same and will be about 240 volts phase-to-phase.
If you were to measure line-to-ground, then you will see 120 volts to ground on lines 1 and 2, but 240 volts to ground on line 3.
Most 3-phase loads don't care about the line-to-ground voltage, they only care about the line-to-line voltage.
All standard phase converters will put out a three-phase voltage based on the utility voltage you supply them. There is a very good possibility you will be supplying the converter with 240 volts AC single-phase so you will get 240 volts AC three phase out.
You will need to confirm that your equipment can and will operate at 240 volts AC three-phase. If your equipment requires a different voltage you would have to install a transformer after the phase converter to step the voltage up or down to match the voltage requirements of your machines.
All phase converters are high leg delta so if the nameplate shows that it requires a three-phase four-wire circuit then you will need to use an isolation/distribution transformer to create a real neutral at a zero potential and balance all three phase voltages to ground.
CAUTION!!! - The place where this is important is when you are hooking up equipment that references ground. CNC machines and electronics have been known to have issues with this.
In summary, it is totally normal to have the manufactured 3rd line read much higher to ground than the utility lines 1 and 2. Most equipment does not care about this because most equipment doesn't reference ground -- it only references the potential between the lines. Special care needs to be taken when hooking up equipment that needs to reference ground, like electronics or CNC machines.
Awesome sales and even better after sales service. I highly recommend Electram!
- Brent Electrical Contractor
You can actually talk to people who know what they are doing, didn't oversell, shipped everything quickly.
Fantastic experience. I took a long time to decide but they were always there to answer all my questions. Can only recommend Electram
- Juerg Owner of Woodworking Shop
I bought a unit from these guys last year. Excellent service,above and beyond! I was in a jam needed it in a hurry and they got to me here in B.C. Quick response and very knowledgeable would buy from them in a heartbeat.
- Jody Business owner
The team at Electram benefits from having an incredibly diverse set of skills, and is organized in a way to produce nothing but the best. Everything that goes out the door is checked and rechecked, quality control is outstanding, and they have a wealth of knowledge that they take the time to share with anyone who asks. Highly recommend.
- Jake Electrical Contracor
Ron and the team at Electram provide outstanding customer services and high quality products. I would highly recommend them to other electrical contractors, engineers, or anyone needing their services. Very satisfied and hope to work with them again soon.
- Jesse Owner of Woodworking Shop
Electram was extremely patient with all my questions and very very knowledgeable. Very happy to have found them.
- Tamara Small Business Owner
I purchased a used Electram phase converter on Craigslist and needed help with the connections. The Staff at Electram responded to my emails and phone call immediately and were very helpful answering all of my questions, getting my phase converter up and running quickly. Great customer service. They even has all of the original specs and info on my exact converter.
- Mark Small Business Owner
Thank you for intense service and parts delivery. You people were knowledgeable, patient and helpful. From ordering parts at 4 pm EST and receiving them the next day by noon, not once but 3 times! Absolutely amazing. And a special thanks to Ron as we were troubleshooting a very tricky application. Our customer was very happy and impressed.
- Tony Owner of Orser Technical Services
Fantastic technical and sales support. Really highly recommend these guys!
© Copyright 2021, Electam | All Rights Reserved.